The state of Lower Saxony plans for the Hannover Medical School the new conversion and extension of Technischen- and medical gases, depending on their use as pharmaceuticals and Medizinproduktegestzt (AMG. MPG) and DIN EN ISO 7396th
Medical compressed air 5 bar: air for ventilation purposes in a quality according to the European Pharmacopoeia. Medical compressed air 8 bar: air for driving surgical tools in a quality according to the European Pharmacopoeia.
Laboratory compressed air: air to supply the laboratory building in a quality similar to that of medical compressed air in the pressure levels 5 and 8 bar. Technical compressed air: air for the operation of pneumatic control and measuring systems as well as for the laundry operation, trash compactors, sterilization and kitchen facilities.
Construction of a 2-circuit supply structure for medical air.
Approximately 2500 m loop, approximately 1 500m building connecting cable. Establishment of new air compressors for medical air. Renewal of transfer stations for the technical compressed air approximately 34 stations. Exchange or disassembly of valves in technical air supply. Reorganization measures existing Notversorgungsnetz, partial replacement of pipes and decommissioning unused line sections.
Construction of a 2-circuit supply structure for the distribution of medical oxygen.
- Approximately 3 500 meters loop;
- Approximately 1 500 meters building connecting cable. Adjustments to the oxygen-cold gasification plants on buildings K16 and the building L.
Construction of centers for technical oxygenation.