PCC Rokita SA | Published June 13, 2015
PCC Apakor Sp. z o.o.
The subject of the call is "execution, delivery, unloading and installation of the water condensates V-23200800, together with its isolation" within the PCC Rokita SA in Brzeg Dolny (56-120) Sienkiewicz Street 4, according to the design documentation developed by the Group Azoty Polish Chemical Consortium Sp. z oo, in terms of: - Industry Cameras - Condensate and caustic wypadowego V-23200800, no studies: - 1201-02.08-501 REV.B. - 1201-02.09-515 Rev.B, - 1201-02.09-516 REV .B - 1201-02.09-517 - 1201-02.09-518 Rev.B - 1201-02.09-519 - 1201-02.09-520 - 1201-02.09-521 - 1201-02.09-522 - 1201 -02.09-523 - 1201-02.09-524 - 1201-02.09-525., - 1201-02.09-526 - 1201-02.09-527 - 1201-02.09-528 - 1201-02.09-529 - 1201 -02.09-530, - 1201-02.09-531, - 1201-02.09-532, - 1201-02.09-533, - plans and sections bowls, - 1201-00.05-05; 2. The general scope of work includes: - the execution and delivery to the premises of PCC Rokita SA tank - hot insulation performance, - installation of the water in the basin of reinforced concrete on the item. approx. -5,5m, - providing as-built documentation; 3. guidelines of hot insulation: - thermal insulation (eg. The type of Isover Ultimate), - thermal resistance> 400 degrees C, - bulk density of> 80 kg / m3, - tolerance thermal conductivity + 0 / -10%, - flammability> B2 ( DIN 4102 or equivalent), - net oplotcza: hexagonal wire> 0.7 mm - required thermal conductivity: 0,052-0,047 W / mK - protective coat - plate: Al-Zn coated on both sides coating, 55% Al, 43, Zc 4%, 1.5% Si), - coating thickness> 20 microns - the thickness of the sheet 0.8-1 mm - insulation must be done in a waterproof, - flashings should be sealed with silicone putty, 20-30 cm - insulation supporting structures should be arranged along the axis of the tank at not less than 1 m,