"Obtaining industrial boiler / 2014."
Budapest Airport, Budapest Liszt Ferenc Nemzetközi Repülőtér Üzemeltető Zártkörűen Működő Részvénytársaság | Published August 23, 2014 - Deadline September 22, 2014
Delivery minimum of 12.5 MW hot water boilers, installation and maintenance during the warranty period. Budapest Airport Zrt. Kazánjaiból in the existing hot water heating plant is planning to replace two pieces. The new hot-water boilers each with a minimum of 12.50 MW, integrated flue gas heat licensee alternative fuel (natural gas, TU5 / 20 industrial fuel oil) burner, complete with automatic controls need to have. The original supplier is responsible for working with the necessary planning, permitting, transportation boiler, the boiler is installed and integrate with existing mechanical and electrical systems in a way that ensured continuous supply of heat to the airport, as well as maintenance and repair during the warranty period of the boilers. Bidder participation in this call megajánlhat compliance with the minimum requirements set out equivalent solutions. Contracting to purchase the subject matter of information only gives the following additional minimum technical requirements: - The nominal power is supplied to the boiler type with integrated flue gas heat licensee (ECO), a minimum of 12.5 MW (only equivalent, or more possible); - Integrated design condensing flue gas heat recovery (ECO) nominal capacity of the gas plant at 50 ° C for a return temperature: at least 400 kW (only equivalent, or more possible); - Combination boiler and combustion control minimum continuous power is available (for gas firing): Up to (<=) 20%; - Boiler and integrated flue gas heat recovery combined (ECO) is guaranteed combustion efficiency of gas-fired mode 100% and 50% under load (at 50 ° C return temperature): 100% for> = 96.5%, and 50%> = 97% . - Minimum return temperature entering the boiler stump: up to (<=) 60 ° c; - Boiler insulation thickness: minimum (> =) 120 mm;=)>=)>