Electrical work for the basic repair of old internal medicine such as:Electrical installation, lightning protection, fire protection.
BVH Ernst Moritz Arndt University Greifswald (EMAU)The building is a basement 4-storey building with hipped roof.
Electrical engineering300 m, 1 040 m, 550 m,
- 1 NSHV with 22 fuse switch disconnectors,
- 17 sub-distributors as wall and stand distributor, sheet steel encapsulated,50 100 m cable NHXMH-J to 5x4mm
DN100, flexible,1 000 Schucko sockets, CEE and installation switch
BR-channel, UP masonry, AP,120 motion detectors for lighting, 750 m parapet channel 210x70mm with and without brackets, off
Galvanized steel, coated (white RAL 9016),620 m LF duct up to 150x60mm made of galvanized steel, coated
(white RAL 9016),Fittings with divider
and mounting with wall bracket / C-profiles on ceiling panels,100 m vertical ladder up to 500x60 mm vertical mounting on wall,
- 51 escape sign lights in permanent circuit and 12
Safety lights in standby mode with single battery,980 luminaires for 3 staircases, corridors, cellars, technical surfaces outdoor lighting, WCs,
Pumi, office and seminar rooms, 1 auditorium,106 Fire Protection Insulations S90 for Core Drilling in Masonry up to Ø 250mm and
Wall thicknesses up to 900mm,20 fire protection shutters S90 up to 0.2m
Version, I30 / I90.