Managing of 2.BA Electrical Melaten.
Other documents are made available, they can be downloaded from www.evergabe.nrw.de.
Managing of the address in II.1.4 construction project with the following services:
Commissioning Management (project steps 2-4).
The appointment is optional stages.
the services listed below are Advertised:
- maintenance cleaning of floors -1 and -2,
- cleaning operations (as required)
- after construction (as needed).
The surfaces to be cleaned, refer to the book room (see. Appendix 1).
Construction of a new training facility Born U21 ZGeoBw
Gersdorff barracks Euskirchen.
LB 002 / Excavation
- excavation: Loosen soil / - Install 5,425 m
LB 013 / concrete work
- STB foundations / - floor panels, in-situ concrete 1 110 m
- STB walls / - supports situ concrete 680 m
- STB ceiling / - joists / - coatings, in-situ concrete 1080 m
- STB staircase constructions situ concrete 15 m
- STB FT-21 flights of stairs St.
- reinforcing bars, BST 500 S (B) according to DIN 488 610 t
- welded steel mesh, BST 550 M (B) according to DIN 488 275 tonnes
LB 017 / Stahlbauarbeiten
- Structural steel 58 t
LB 018 / waterproofing
- cleaning, primer, seal 9220 m
Engineering services for building services (LP 1-8), investment group 4 acc. HOAI § 55 "Engineering services TGA" for expanding the replacement power system of the building BTZ on the grounds of the University Hospital of the RWTH in Aachen.
Engineering services (services for the TGA in accordance with § 55 HOAI) for the extension of the replacement power plant:
To ensure the future safe and reliable emergency power operation at elevated load situations an increase in the existing spare capacity in the network replacement power ring of the University Hospital Aachen is required. Current load flow calculations from 2016 have shown that the existing emergency power supply to the EN-ring at the medium voltage level at further integration of new stations can not ensure full power supply in case of power failure.
For the integration of projects, Surgical Intensive Care (OIP), primary data center 1, new energy center, surgical center in the EN-ring is for the future safe and reliable emergency power operation at elevated load situations a short-term Leistungshöhung the existing spare network capacity required.
Through additional 10 kV network replacement units outside the building BTZ-N a power increase of replacement power performance at Aachen University is to be implemented. With the connection of two additional emergency power generators outdoors (10 kV / 2500 kVA in container construction) in the existing plant in the building BTZ-N, is particularly a short-term power increase for the 10 KV EN-ring at Aachen University are implemented.