Auvere power facilities, buildings and facilities, ventilation and air conditioning maintenance
Eesti Energia Narva Elektrijaamad AS - Natalja Beljajeva | Published November 25, 2015 - Deadline December 11, 2015
Systems of industrial purpose, ie, the power plant must ensure the reliability of technological equipment. Systems management is carried out by means of a corresponding controller 13 on the control of the building. The volume of work: 252 Total includes servicing the system, of which 121 of the ventilation system and the air valve 80, 35 and 16 air heaters air-conditioning system, in addition to the 60 fire protection valves. In response to the time required for ventilation and air-conditioning system for the elimination of defects, from receipt of the notification time: 2 hours. The list of work equipment, technical maintenance: Includes all operations in the performance of the devices valmistamise-, over use of the manual and the technical service: control boards work and automation equipment configuration checking, testing, control devices (PDS, and temperature sensors), if they raise doubts about the readings. Prevention work rotating mechanisms (control of vibration, a belt-tightening, lubrication of bearings). Prevention of actuators (manual and automatic control of their work mode, switches Setting the lubrication of moving parts). The latch-reguleerarmatuuri prophylaxis (reguleerimisklappide the work of inspection, lubrication of moving parts). Cleaning water filters, air filters, exchange. Check the operation of the circulation pumps. In addition, the volume of works to be performed include: Thermal insulation and insulation of the metal coating and the dismantling of the installation (and, where necessary, in small volumes), excluding equipment warranty repairs are not related to thermal insulation and the replacement of the metal coatings. Materials and spare parts required for servicing the transport, loading and unloading. During a service the refuse, scrap metal and the like. cleaning. Intra-station thermal testing programs, participation in networks. (2 times a year), Air-conditioning heat exchangers, compressed air purification, the Contractor shall use the dust collection equipment. Inspection of fire dampers. May 2010, a., § 42.). Air-conditioning service, substances formed during the Cold gathering, export and disposal. The Contractor must comply with their obligations under the kekkonnaministri Regulation No. 25 of 11.07.2012 "fluorinated greenhouse gases and ozone-depleting substances in products, equipment, systems and tanks, and handling may register the statutes and rules of keeping and reporting procedures and forms". The contractor must carry out in accordance with the licensing requirements of its fluorinated kasvuhoonegaaaside service generated during the refrigerant collection, extraction and utilization. Necessary equipment prior exchange of coordinating with Customer.